Review by: J. A. B.
Work Description: diagnosis of boiler furnace problem and replacement of faulty thermostat.
Comments: Very competent service personnel. Friendly, efficient, and honest.
Review by: J.
Work Description: Cleaned and changed filter on furnace
Comments: was told he would come at 8:30 or 9:00 a.m. and he arrived early at 8:00. He was early which for me was not a good idea. He was very good with the furnace and knew what he was doing. In and out in under an hour, neat and reasonablly priced($109). We have a TRANE FURNACE and a special filter whic is more expensive.